Review us on Google
Review us on BirdEye
Like us on Facebook!
About Mason Heating & Air
We at Mason Heating & Air are dedicated to delivering high-quality service at price rates that are fair and affordable in Mason, OH. We strive to continue our reputation as a trustworthy, high-quality HVAC company you can count on throughout the Greater Cincinnati, Ohio, area. We appreciate you taking the time to learn more about our family-oriented company built on values, and our vision to provide unparalleled products and services throughout our wonderful communities.
Altogether, our technicians have more than 45 years of combined industry experience that can resolve any and all HVAC situations with high-quality affordable solutions. Our top-notch team of techs has installed hundreds of AC units, furnaces, heat pumps, indoor air quality devices, and more. Our service team is knowledgeable, kind, friendly, hardworking, and fast.
Located a few miles from Kings Island Amusement Park, Mason, OH is the largest city in Warren County, with more than 30,000 residents. Mason City Schools has consistently rated as one of the top school districts in the state of Ohio. There are many reasons why Mason Heating & Air is proud to serve the hardworking people of Mason with quality residential Heating, Cooling, and Indoor Air Quality Services. We also extend these products and services to surrounding areas, enabling us to bring the Five Star Difference to the entire area! When your heating or cooling system breaks down, you can rely on Mason Heating & Air. We’re confident in our skills, so you should be too. We look forward to working with you
for Mason, OH
I removed a Goodman heat pump and electric air handler. I installed a Carrier Multi-Speed X-13 2 Ton Electric Furnace and a Carrier 15 SEER 2 Ton Heat Pump. Cycled and monitored the system. Operating normally at this time. Included with the installation is a free 1 year service maintenance agreement.
Found furnace locked out due to high limit being stuck open/was able to tap limit and get it to close. Also found pressure switch not closing/collector box was completely filled with water Due to a clogged condensate trap. Pulled and cleaned condensate trap. Ignitor-90ohms (needs replaced) Blower cap-8.9/10 (needs replaced) High limit needs replaced. Pulled and cleaned flame sensor. All drain lines going to and coming from condensate trap need to be replaced due to being in poor condition.
Service work performed: BLOWER CAPACITOR READING LOW/RECOMMENDED REPLACING IT. BLOWER WHEEL IS VERY DIRTY/NEEDS PULLED AND CLEANED. THERMOCOUPLE WILL NEED REPLACED SOON, HAD TO LIGHT PILOT A COUPLE TIMES TO GET IT TO GO AGAIN. FILTER ALSO NEEDS REPLACED OR FURNACE WILL OVERHEAT.
Service work performed: System was operational at arrival. Pulled and cleaned flame sensor Inducer motor cap-2.6/3 LOW RECOMMEND REPLACING. Ignitor-50.6ohms OK Blower cap-19.7/20 OK Board has a lot of water damage/could have an intermittent issue. Inducer motor has a hard time starting up/bearing are starting to fail. Ran new drain line