Review us on Google
Review us on BirdEye
Like us on Facebook!
About Xenia Heating & Air
We at Xenia Heating & Air, are truly honored and proud to be part of the Greater Greene County, Ohio, area and beyond. We offer our fellow community members, homeowners, a vast array of HVAC solutions for all types of situations, needs, and budgets. From day one, our company’s vision and mission have been to offer the absolute highest quality heating, cooling, and Indoor Air Quality products and services at price rates our competitors cannot beat.
From our humble origins, our philosophy has always been to offer the most value possible at price rates that can’t be beaten — to maintain, service, sell and install the best, most reliable HVAC equipment in the industry. One of the strongest assets of our business is the level of service we provide our customers, services that are ever-improving as we continue to grow and evolve in the heating, cooling, and air quality business.
We at Xenia Heating & Air want you to know that you are not just a customer to us; you are a valued client, a fellow community member, and your safety, comfort, and satisfaction is our top priority. It is our honor to provide the very best service to meet the needs of you and your loved ones so you can rest assured with peace of mind knowing you chose the right team, no matter what reason for calling.
Our Customer Satisfaction Guarantee is backed by our word. Because of this, you can enjoy the complete peace of mind that comes with knowing that we always stand behind every bit of our work. Our service technicians and installation specialists are highly-skilled and friendly and all the work they do is always 100 percent backed by this guarantee — in addition to being backed by our insurance. Furthermore, because we carry all the top-quality brands for all your HVAC needs, you can have confidence your situation will be handled professionally and everything is 100% guaranteed and new systems always come with warranties as well.
We are ever-striving for the highest standards of quality, workmanship, and customer service, above and beyond what most HVAC contractors provide. Additionally, we provide all of our customers with NATE- certified technicians, extended customer service hours, competitive pricing, emergency repair services, warranties and we consistently maintain a high score among customer reviews.
We at Xenia Heating & Air have established strong, long-standing relationships all with the major manufacturers of residential HVAC equipment. Because of these long-standing ties, we are able to offer our customers the highest quality products available at prices that can’t be beat. We are also able to ensure all of your HVAC needs are met using the latest technology to ensure your system will run flawlessly for many years to come. We take pride in always being able to provide our customers with the best brands and the latest innovations, keeping us ahead of the curve in the HVAC industry.
for Xenia, OH
Ron - Xenia, OH
Friendly and knowledge of our furnace.
After removing the Carrier gas furnace and air conditioner, I installed a Carrier 80% 110,000 BTU Gas Furnace and a Carrier 13 SEER 4 Ton Air Conditioner. Cycled and monitored the system. Operating normally at this time. Included with the installation is a free 1 year service maintenance agreement.
Commercial Roof System. Job had to be rescheduled due to inclement weather conditions and safety of personnel.
I completed a diagnostic on a Ruud gas furnace. Determined that the flame sensor was not installed correctly. I cleaned and installed flame sensor correctly. I also determined that the spark ignitor spliced and needs to be replaced. Parts to be ordered. Cycled and monitored the system. Operating normally at this time.
I completed diagnostic on a Duquesne furnace. Determined that the unit was shutting down a pressure switch code. Determined that the flue was disconnected at the ceiling. Reconnected the flue. Cycled unit. Monitored operation. Unit shut down again on a pressure switch code. Checked the condition of the flue in the attic and on the roof. On the roof found that the Vin cap venting was partially obstructed which was too far down to adjust. Removed vacuum hose from the inducer motor and cleared vacuum nipples and reattched. Recommended that the client have the blower motor cleaned. Client declined to have blower motor cleaned. System operating normally at this time.
Installing full system
Installing full system
Installing full system